I have recently conducted both an onsite audit where a Dyson Airblade was installed and a desktop audit where one of these units has been specified.
It is my opinion that Dyson Airblade hand driers should not be used within accessible (disabled) toilets as they are not usable by a person with a disability.
Photo of Dyson Airblade installed within an accessible toilet Also note the tap provided is not compliant)
Whilst Australian Standard AS1428.1, clause 15.4.3 nominates the height for hand dryers that are provided within accessible bathrooms, it is silent on the design of such fittings.
15.4.3 Soap dispensers, towel dispensers and similar fittings Where provided, soap dispensers, towel dispensers, hand dryers and similar fittings shall be operable by one hand, and shall be installed with the height of their operative component or outlet not less than 900 mm and not more than 1100mm above the plane of the finished floor, and no closer than 500mm from an internal corner.
The key issue is “reach range”
There is nothing like the threat from a disgruntled stair nosing supplier to sue me if I do not retract...read more
The recent Supreme Court of Victoria ruling makes clear that Victorian owners corporations are required...read more
The use of ‘Expert Judgement’ when assessing a Performance Solution in regard to disability access can leave practitioners open to potential claims under the DDA. Th...read more